- Ideas & How-Tos
Choose Your Savings
Prices, promotions, styles, and availability may vary. Our local stores do not honor online pricing. Prices and availability of products and services are subject to change without notice. Errors will be corrected where discovered, and Lowe's reserves the right to revoke any stated offer and to correct any errors, inaccuracies or omissions including after an order has been submitted.
Do-it-yourselfers can install CTS (copper tube size) CPVC (chlorinated polyvinyl chloride) pipes and fittings with a little help from Lowe's.
Product costs, availability and item numbers may vary online or by market.
Missing anything? Shop Online
Take notice of some of the tools and materials list before you begin.
Don’t allow cement to puddle or accumulate inside the system. Solvent cement should conform to the appropriate ASTM standard for the piping system (see the solvent cement manufacturer's recommendations). All-purpose cement isn’t recommended.
Cut the pipe square with the axis.
Remove burrs and bevel the end of the pipe 10 to 15 degrees.
Dry-fit the pipe. With light pressure, the pipe should go 1/2 to 1/3 of the way into the fitting hub. Don't use pipe and fittings that are too tight or too loose.
Use an applicator to apply sufficient cement into the inside of the fitting. The applicator should be 1/2 the size of the pipe's diameter.
Coat the surface with primer by applying a full, even coat of cement on the outside diameter of the pipe and to the inside hub of the fitting. Again coat the outside of the pipe. Primer isn’t necessary for CTS pipes, but check with your local plumbing codes.
While the cement is fluid, insert the pipe into the fitting hub, giving a quarter turn to ensure full distribution of cement within the joint. Allow the joint to cure prior to hydrostatic testing.
Follow the manufacturer's recommendations for set and cure times as well as for primers and cements.
Primers and cements are extremely flammable and may be explosive. Don’t store or use primers or cements near heat or an open flame. Ignition of the solvent vapors caused by spark or flame may result in injury or death from explosion of fire.
Solvent fumes created during the joining process are heavier than air and may be trapped in newly installed piping systems.
When working with cements, primers and new piping systems, provide adequate ventilation to reduce line hazard and minimize inhalation of solvent vapors.
Testing with or using compressed air or gas in PVC / ABS / CPVC / cast-iron pipe or fittings can result in explosions and cause severe injury or death.
Never test with or transport / store compressed air or gas in PVC /ABS / CPVC / cast-iron pipe or fittings.
Never test PVC /ABS / CPVC / cast-iron pipe or fittings with compressed gas or air over water boosters.
Only use PVC / ABS / CPVC / cast-iron pipe for water or approved chemicals.